When it happens, there’s nothing more stressful than a broken AC in the middle of summer or heating problems just as temperatures start to drop–especially when those problems lead to higher energy bills and poor indoor air quality. Midwest Comfort Heating & Cooling is the Addison, IL HVAC company to call when it comes to fast turnarounds and hassle-free service. We will work closely with you to discuss your needs and present you with the best solution based on your needs.
Give us a call today for immediate heating and air conditioning services in Addison, Illinois.
We offer comprehensive heating, AC, and indoor air quality solutions–from boiler installation to heat pump repair to ductwork and everything in between. Whether you need help with a minor repair or you are looking to get an estimate on a new system installation, our experts will take the time to go over your needs and help you determine the most cost-effective solution for your home.
Call today to book an appointment for fast and reliable heating and AC services in Addison, IL.
We know how frustrating it is to struggle with indoor comfort problems and high energy bills. At Midwest Comfort Heating & Cooling our goal is to make sure you receive the quality solutions you need to achieve whole-home comfort. Through honest and transparent services, solid workmanship, and a worry-free experience from start to finish, we’re here to deliver the exceptional results you deserve–so you can finally enjoy the comfort and peace of mind you need.
Contact us today to discuss your HVAC needs and schedule immediate service for AC or heating repair or installation in the Addison, IL area.
Always good service and fair prices
Midwest Comfort is great. I would recommend them to anyone. I've been a customer for years.
Great service; fair price; would highly recommend: will definitely call for future work on any HVAC matters.
HVAC service call for no cooling. Found AC with significant leak and frozen coil. Old American standard ac coil was frozen and leaking into furnace. System is very low on r-22 refrigerant. Quotes and sold new equipment with a rheem 13 seer Ac, and a single stage constant torque 75k btu furnace
HVAC installing We installed a Rheem Ruud u96v 2 stage variable speed 96% furnace, ra13 13 seer air conditioner and matching evaporator coil. We added an Aprilaire 700 humidifier For indoor air quality we installed iWave air purifier and Air Scrubber UV system.
Service call for furnace not working. Found ducane gas furnace with dirty flame rod. Clean and preformed preventative maintenance and cleaned the unit. Quoted new air conditioner system rheem 13 seer And 14 seer. Service and estimates in elk Grove village.
Air conditioner tune up and preventative maintenance. Cleaned outdoor condenser coils and changed aprilaire high efficiency Merv 11 filters. Cleared drain lines and flushed. Checked pressures, subcooling. Compressor, and capacitor output. In Elk Grove village Mt.Prospect Arlington Heights area
No heat service call on Goodman furnace in Elk Grove Village.
Quote Ruud furnace and AC in Elk Grove Village.
Magic pak through the wall package unit. Unit it leaking water due to a clogged condensate drain, and supply isn't insulated causing water to leak over unit. Will return to clean condenser coil, insulate supply, and put in a return grille with a filter slot 16x16x1
Ac clean and check, tune up. Checked aprilaire high efficiency filter and cleaned American standard unit. Also checked refrigerant levels and capacitance along with vital component amp ratings. Cleaned unit with chemical cleaner for best results.
Diagnosis and repair on Air conditioning unit. Fixed low voltage short, and cleaned the condenser coil
Diagnosis on no cool. AC not running, found low voltage short and blown fuse. Found short, rewired and replaced fuse on circuit board.
Lennox 80% gas furnace clean and check, preventative maintenance found hi limit bypassed and signs of flame rollout and cracked heat exchanger, quoted and recomended new unit.
Preventative Maintenance and clean and check on Ruud 80% efficient gas furnace. Replaced Aprilaire 810 filter and Aprilaire #35 pad with humidipro water filter to reduce scale and increase longjevity of humidifier Aprilaire 600m