In the Mt. Prospect area, Midwest Comfort Heating & Cooling is well known for providing exceptional ac repair, installation, and service. The people we send out to serve you are also top notch, something you'll see in their reviews below. Everyone you deal with at our company has the goal of making sure your experience with us will be so good you'll call us every time you need help. You can feel confident working with Midwest Comfort Heating & Cooling because we stand behind our work and comply with all local codes. This is why, as you can see by the map and reviews below, we are rated so highly for Furnace and Air Conditioning Repair in Mount Prospect, IL in Elk Grove Village IL. Call us today at (847) 338-2777!
This company has extremely knowledgeable technicians who took the time to teach us about the existing HVAC equipment at our house and all of the options we had for replacement equipment, which we really appreciate as relatively new/inexperienced homeowners! They helped us select the right equipment for our house, budget, and preferences. They also offer reliable service visits so we can get the most out of our investment. I would highly recommend Midwest Comfort for any HVAC or water heater projects.
Diagnosed problem and quick resolve
Very knowledgeable techs, with great service and reasonable prices
This company gives you honest answers, were very quick to getting to my home and fixing my boiler’s issue. Highly recommend them and we will use them again.
These guys have always been good about coming out in a timely fashion whenever we’ve had issues. Great to feel confident they have you covered.
Mark is thorough and explains the problem and repairs to where it is easily understood.
Exceptional service with a good price
They arrived at my phone in a timely manner. The techs were very friendly and knowledgeable. This the only company that I will let service my furnace and air conditioner.
Tells us the problem and shows us
Cole got the furnace working during the polar vortex and Mark and Rene did a great job on the new A/C. Midwest is the best!! Thanks!
Our AC check up was done thoroughly and at a reasonable price. The service men were prompt, courteous and professional. They shared great information regarding my AC units and offered the "Club" option to carry in to a fall check up for our furnaces.
Mark did an awesome job. Thank you!
Competent and they always provide great service.
Excellent and expert service - really appreciate the flexible scheduling.
The tech who is knowledgeable very thorough and polite. Plus he cleaned up The workspace when he was done. Highly recommend these guys
Mark did a great job! He was friendly, helpful, insightful and got our furnace up and working quickly! Thanks again!
Very hardworking and honest. Didn’t have to wait long for service.
They arrived on time, completed installation quickly and left my home clean.
I’ve never been disappointed when I call Midwest Comfort. Most recently they got our A/C back up and running as quickly as possible, going above and beyond.
Midwest Comfort recently completed my Spring AC tune-up and as usual did an awesome job. Highly recommend them for AC and heating work.
Replaced Honeywell Zoning damper in Mt Prospect.
Preventative maintenance AC clean and check. Replaced filter on Aprilaire 1210 model whole home air purifier. Cleaned outside condenser and checked pressures/subcooling.
Preventative maintenance with 21 point inspection on Air Conditioner and AC. Flushed out condensate lines and checked pressures and subcooling on AC system. Cleaned and washed condenser.
Air condition diagnosis for no cooling found a blown dual capacitor from a mouse. Replaced capacitor on Trane condenser now homeowners are cooling.
Service call for HVAC AC air conditioner not cooling. Diagnosis Found flat system and recharged per clients orders.
AC air Conditioning service call for diagnosis. Found low refrigerant charge leading to iced over coil and water on furnace floor. Recharged American standard unit with 2.5lbs of R410-A
AC preventative maintenance clean and check. 21 point inspection for spring air conditioning. Added hard start kit to old Trane with high in-rush amps, and cleaned both outside condensers with a cleaner and removed panels for a deep clean.
Double AC clean and check preventative maintenance with 21 point inspection of air condition and HVAC. Replaced filters, cleaned outdoor units, suggested repairs and gave the units a clean bill of health for the summer.
American standard AC preventative maintenance with clean and check and 21 point inspection. replaced Aprilaire whole hole air purifier filter model #810. Cleaned outside condenser and installed hard start kit for high in-rush amperage.
Ruud AC air conditioner preventative maintenance with clean and check 21 point inspection. Replaced Aprilaire whole home air purifier with Merv 11 high quality furnace filters. Cleaned outside condenser and checked amps/microfarads. And flushed out condensate drains.
Ruud AC Preventative maintenance with clean and check & 21 point HVAC inspection. Cleaned outdoor coil and replaced Aprilaire whole home air purifier filter #810.
Ruud 13 SEER AC and condenser preventative maintenance with clean and check (21 point inspection) Replaced Aprilaire whole home purifier with model #410 Cleaned outdoor unit, and checked pressures.
Reem AC preventative maintenance and 21 point inspection with cleaning of outside condenser. Replaced Aprilaire whole home air purifier filter #213 (Merv 13) Client is ready for summer.
Reem AC air Conditioning PM (preventative maintenance) with 21 point inspection. Replaced Aprilaire 213 filter/whole house air purifier. Cleaned outside condenser and checked pressures. Client is ready for summer
Double unit preventative maintenance and clean and check, with 21 point inspection. Replaced Aprilaire filters model 810 and 410. Added a pound of 410-A to boost subcooling on attic unit. Unwired attic fan for client.
Ruud AC preventative maintenance and clean and check. 21 point spring inspection 13 SEER Condenser.
AC clean and check preventative maintenance. Found low subcooling and added a pound of r-22 along with cleaning the outside American standard condenser
Carrier AC Preventative maintenance clean and check. Cleaned unit and did 21 point inspection. With pressure check and amp draws, capacitor checks, and more. All was operating well. Fan motor amperage was .03 above spec. System is 18 years old though.
Clean and check preventative maintenance for Ruud AC. Condensate pump cleaning with tablets, and cleaned outside condenser along with pressure checks and amp draws, tests, etc..
Ducane 80% efficient gas furnace diagnostic call. Found clogged filter restricting air flow to unit, causing overheating. Reccomended and preformed a preventative maintenance, and clean and check. Replaced Trane humidifier with new Aprilaire pad.
Diagnosis on Aprilaire 700a. Cover wasn't on correctly leading to uncomplete connection at molex plug inside* outdoor temp sensor was dialing down RH due to low outdoor ambient temps.
Payne 80% gas furnace diagnosis call for noise. Found aging inducer with play in the wheel, high amo draw and bad bearings. Quoted new unit as furnace is 14 years old and oversized.
Burnham boiler no heat call. Found bad circulator pump.