In the Mt. Prospect area, Midwest Comfort Heating & Cooling is well known for providing exceptional ac repair, installation, and service. The people we send out to serve you are also top notch, something you'll see in their reviews below. Everyone you deal with at our company has the goal of making sure your experience with us will be so good you'll call us every time you need help. You can feel confident working with Midwest Comfort Heating & Cooling because we stand behind our work and comply with all local codes. This is why, as you can see by the map and reviews below, we are rated so highly for Furnace and Air Conditioning Repair in Des Plaines, IL in Mt. Prospect IL. Call us today at (847) 338-2777!
Great! Very thorough.
Tech arrived on time and was professional. Installed new thermostat and made sure all was working properly.
Clean and check with preventative maintenance on AC unit. 21 point HVAC inspection found low dual capacitor. Replaced capacitor and cleaned outdoor condenser.
Preventative maintenance and clean and check inspection on Carrier AC and condenser. 21 point inspection, with cleaning of outdoor coil.
Furnace repair. We replaced an oem 95% Carrier inducer motor
Clean and check preventative maintenance on 80% Comfort Master. Replaced hot surface igniter and diagnosed bad honeywell humidifier.
Lennox furnace no heat service.
No heat call. Diagnosis found severly cracked heat exchanger was tripping the rollout safety switches, new gas furnace needed.
Replaced humidistat sensor that had grounded out and failed for a Aprilaire 600, series automatic humidistat and humidifier.
Clean and check maintenance on an 80% Rheem gas furnace. Inducer was rusted out and in bad condition. Reccomend new unit with estimate and quote
Clean and check tune up on Rheem 80% gas furnace. Aprilaire humidifier 500 series had a faulty solenoid valve which I replaced along with the water panel.
Free Quote & estimate on new furnace and AC bundle
Heil 90% Clean and Check tune up with aprilaire humidifier pad replacement.
Carrier furnace cleaning and safety check
Full installation of Rudd Furnace and air conditioning with April Aire air cleaner and humidifier.
Ac service call. We performed service on a Carrier air conditioner and cleaning the condenser coil